Air Conditioner Gas Top Up Kuala Lumpur & Selangor
When we check your system if gas refill is needed we do air conditioner gas top up for your system. Air conditioner gas top up is part of the regular maintenance service to the unit. Without the gas system can’t be checked.
Professional technicians put special gage into the outdoor unit (picture 1). There are special ports which you can attach those special gauges connectors for reading right values (picture 2). One of them should be connected to the low pressure point (Blue hose); other one will be connected to the supply point which is for the refilling the refrigerant. (Yellow hose)
First of all technician should read the gas level of the system. If there is lack of gas in the system, reason could be small leakage. This leakage should be found out and repair. Reason could be loose nut connections, torn rubber seals, one of the stop valves or the worst case could be small hole in the evaporator coils i.e. after this recovery technician put sufficient gas into the system.
Professional serviceman will fix the small hole using torch light and welding stick if there is small leakage found in evaporator coils. This is the part of repair the unit.
After fixing the leakage, technician be sure that in the supply line (Yellow hose) there should be a vacuum. After applying suction from that end of the system, old compressor can be used to create vacuum (picture 3) technician should see vacuum of 30 as seem in the picture 4.
After that supply hose (yellow hose) taken off from old compressor which made the vacuum into the supply line(yellow hose)than it will be connected to the gas tank (picture 5).
While air conditioner unit is running, tank valve opens and refrigerant sucks into the system by the running compress itself. Proper value should be seen is 60 pressure while unit is running. (Picture 6) this is how air conditioner gas top up is done.
Call us for your system check. We will do air conditioner gas top up if your system needed with proper gas.
Price Schedule KL & Selangor
"Affordable Service from RM 70 onwards, 100% moneyback satisfaction guarantee"
for a no obligation quotation now
|Wall Mounted Units||Ceiling Units|
|1 HP||1.5 HP||2 HP||2.5 HP||3 HP||3 HP||4 HP|
|General Service||RM 70||RM 75||RM 120||RM 120||RM 150||RM 150||RM 150|
|Chemical Wash||RM 130||RM 150||RM 150||RM 150||RM 150||RM 320||RM 550|
|Installation||RM 250||RM 300||RM 400||RM 440||RM 500||RM 500||RM 670|
|Gas Top up||RM 115||RM 115||RM 115||RM 115||RM 115||RM 115||RM 115|
|Dismantle Old Unit||RM 75||RM 75||RM 100||RM 100||RM 125||RM 200||RM 250|
Why Choose Us
100% Money-back Guarantee
Enjoy a total peace of mind when you hire us. Because we offer a "100% money-back guarantee" assurance when you engage our service - so there is ZERO risk on your part!
FREE Site Survey
Our service also includes a complimentary site survey to better understand your air conditioner unit service needs so that we can give you the most accurate quotes.
Their technicians were very helpful, courteous, updating us on the job progress frequently and very communicative. This was my third time using their services and they are real professionals. I am extremely satisfied with their performance all this while and they are courteous. I will recommend them to others.Nedim Alibi
With the complete and thorough job by your team in your recent inspection and maintenance schedule the other day, we were indeed very satisfied with their performance. So happen they also discovered a problem with the air cond and after recommending to us whom we agreed, it was done beautifully indeed.Tan Lee Lee
I had some issues with my air conditioner leaking on a Saturday and we felt great the service techs who came and repaired it on the spot. He was doing such an excellent job, explaining to me on the things to be done. In a matter of hours, our air conditioner was back to normal. They did such a fantastic job!Noreen Noor